You can manage system disables, zone disables and point disables at the 4100ESi panel.
A disabled condition can occur when an operator takes a component out of service to prevent a nuisance alarm, when maintenance is being carried out in an area, or if the component is faulty and is undergoing repair. The following should be noted about disables:
- Faults are not displayed for disabled components.
- Alarm, Priority2, or Monitor statuses are not displayed for disabled detectors.
- Disabled outputs are forced off and cannot be activated under automatic or manual control.
- Some types of system point cannot be disabled.